Explosion-proof manual pull station IP-535-GORELTEX1-B is intended for constant all-day operation (possibility to send alarm signals in fire alarm loops when activating the actuating member) in fire alarm and fire suppression systems as a passive element for operation together with receiving and control devices.
The pull station may be applied as a single element; there is an option of series connection to fire alarm loop of a group of pull stations.
Alarm announcement mode of IP-535-GORELTEX1-B pull station is switched on by pressing the button after pulling out of the protective element. Return of the pull station to initial position (standby mode) is carried out by means of a key. The pull station may be switched to alarm loop with normally closed and normally opened contacts.
IP-535-GORELTEX1-B explosion-proof manual pull stations may be operated in working condition in various climatic areas, they are supplied with various cable glands. The pull station design and its manufacturing technology, as well as highly-reliable switches, intended for multiple switching on and off, ensure failure-free operation during practically endless period of time.
Full production cycle from foundry patterns to finished products is carried out by explosion-proof equipment plant “ZAVOD GORELTEX” Co. Ltd. (former “CORTEM-GORELTEX” Co. Ltd) in the territory of the Russian Federation.
Scope of application – underground mines and pits non-hazardous with gas (methane), coal dust; outdoor and indoor hazardous areas as per explosion protection marking, GOST 30852.13-2002 (IEC 60079-14:1996), areas with presence of combustible dust, as per GOST IEC 61241-3-2011, dangerous production facilities of I, II, III, IV hazard class supervised by Rostechnadzor of the RF and national technical supervision bodies of the Customs Union and CIS countries.
|IP-535-GORELTEX1-B||-||Х||-||Х||/||Х||– TU 26.30.50-050-72453807-2017|
01 - one normally closed contact
10 - one normally opened contact
11 - normally opened + normally closed contacts
02 - two normally closed contacts
20 - two normally opened contacts
03 - three normally closed contacts;
30 - three normally opened contacts
01+20 - one normally closed contact + two normally opened contacts
02+01 - two normally closed contacts + one normally closed contact.
|Dimension type of cable gland (max. 2 pcs.)|
|Options, accessories and versions|
Example: IP-535-GORELTEX1-B-20-KNV2N-TU 26.30.50-050-72453807-2017
Connection diagram (opening, series connection)
Connection diagram (closing, parallel connection)
|Type of fire alarm control panel||Parallel connection (closing)||Series connection (opening)|
|LB-07||Rd shall ensure current consumption
>15 mА, Rок = 2 kΩ, VDоk = KD522
|Rd = 11 kΩ, Rоk = 2 kΩ, VDоk = KD522
|Luch||Rd = 2.4 kΩ, Rоk = 2.4 kΩ, VDоk = KD521А
||Rd = 2.2 kΩ, Rоk = 2.4 kΩ, VDоk = KD521А
|PPK-2||Rd = 1.2 kΩ, Rоk = 3.6 kΩ, VDоk = KD521А
||Rd = 10.0 kΩ, Rоk = 3.6 kΩ, VDоk = KD521А
|Bolid||Rd = 1.5 kΩ, Rоk = 4.7 kΩ, VDоk is not to be installed
||Rd = 8.2 kΩ, Rоk = 4.7 kΩ, VDоk is not to be installed
|Yakhont-16i||Rd = 1.8 kΩ, Rоk = 8.2 kΩ, VDоk is not to be installed
|VERS||Rd = 820 Ω, Rоk = 7.5 kΩ, VDоk is not to be installed
||Rd = 10 kΩ, Rоk = 7.5 kΩ. VDоk is not to be installed
Differences between A class and B class manual pull stations
Differences between A class and B class manual pull stations according to GOST R 53325-2012: A class manual pull station (IP-535-GORELTEX1-A, IP-535-GORELTEX2-A) is activated after displacement of indestructible actuating member, which is followed by change of appearance of the pull station.
B class manual pull station (IP-535-GORELTEX1-B) is activated after completing of two actions:
1. provision of access to actuating member by means of destruction or displacement of actuating member, made as A class actuating member;