Explosion-proof manual pull station IP-535-GORELTEX2-A is intended for constant all-day operation (possibility to send alarm signals in fire alarm loops when activating the actuating member) in fire alarm and fire suppression systems as a passive element for operation together with receiving and control devices.
The pull station may be applied a single element; there is an option of series connection to fire alarm loop of a group of pull stations. Only a signal from one pull station is sufficient to issue the command from central panel for switching on fire extinguishing systems. The pull station may be applied in hazardous areas of 0, 1 and 2 classes according to GOST 30852.9-2002 and GOST 30852.13-2002 (IEC 60079-14:1999).
Indication operation mode (located on the top): constant green light emission – standby mode, intermittent red light emission – actuating mode.
Alarm announcement mode is switched on by pulling out safety pin. Return of the pull station to initial position (standby mode) is carried out by installation of the safety pin to its proper location using a special tool (flat blade screwdriver). The pull station may be switched to alarm loop with normally closed and normally opened contacts.
Full production cycle from foundry patterns to finished products is carried out by explosion-proof equipment plant “ZAVOD GORELTEX” Co. Ltd. (former “CORTEM-GORELTEX” Co. Ltd) in the territory of the Russian Federation.
Scope of application – underground mines and pits non-hazardous with gas (methane), coal dust; outdoor and indoor hazardous areas as per explosion protection marking, GOST 30852.13-2002 (IEC 60079-14:1996), areas with presence of combustible dust, as per GOST IEC 61241-3-2011, dangerous production facilities of I, II, III, IV hazard class supervised by Rostechnadzor of the RF and national technical supervision bodies of the Customs Union and CIS countries.
FORMATION OF MARKING
|IP-535-GORELTEX2-А||-||Х||/||Х||– TU 26.30.50-050-72453807-2017|
|Cable gland dimension type (max. 3 pcs.)|
|Options, accessories and versions|
Example: IP-535-GORELTEX2-А-KNV1N-TU 26.30.50-050-72453807-2017.
CONNECTION DIAGRAM OF PULL STATIONS IP-535-GORELTEX2-А TO FIRE ALARM CONTROL PANEL
Connection diagram (parallel connection)
Connection diagram (series connection)
Type of fire alarm control panel
|Parallel connection (opening)
||Series connection (closing)
|LB-07||Rd shall ensure current consumption > 15mA, Rok = 2kΩ, Vdоk = KD522
||Rd = 11 kΩ, Rоk = 2 kΩ, VDоk = KD522
|Luch||Rd = 2.4 kΩ, Rоk = 2.4 kΩ, VDоk = KD521A
||Rd = 2.2 kΩ, Rоk = 2.4 kΩ, VDоk = KD521A
|PPK-2||Rd = 1.2 kΩ, Rоk = 3.6 kΩ, VDоk = KD521A
Rd = 10.0 kΩ, Rоk = 3.6 kΩ, VDоk = KD521А
|Bolid||Rd = 1.5 kΩ (3.0 kΩ - to determine dual actuation), Rоk = 4.7 kΩ, VDоk is not to install
||Rd = 8.2 kΩ (4.7 kΩ - to determine dual actuation), Rоk = 4.7 kΩ, VDоk is not to install
|Yakhont-16i||Rd = 1.8 kΩ (4.0 kΩ - to determine dual actuation), Rоk = 8.2 kΩ, VDоk is not to install
Rd = 820 Ω (1.8 kΩ - to determine dual actuation), Rоk = 7.5 kΩ, VDок is not to install
Rd = 10 kΩ (4.7 kΩ - to determine dual actuation), Rоk = 7.5 kΩ. VDоk is not to install
Differences between A class and B class manual pull stations according to GOST R 53325-2012: A class manual pull station (IP-535-GORELTEX1-A, IP-535-GORELTEX2-A) is activated after displacement of indestructible actuating member, which is followed by change of appearance of the pull station.
B class manual pull station (IP-535-GORELTEX1-B) is activated after completing of two actions:
1. provision of access to actuating member by means of destruction or displacement of actuating member, made as A class actuating member;
2. subsequent manual activation of actuating member.